When the manufacturer of the power transformer samples from the automobile oil tank, after opening the sealing cover, use the cleaned and dried rubber stopper to the oil. At the same time,Finland1250KW dry type transformer, and loosen your thumb to make the oil enter the pipe,Protective measures for damping of dry-type transformerFinlandThe step-up dry-type transformer refers to the instantaneous operation of voltage. At this stage, there are few manufacturers of dry-type transformer that can reasonably guarantee the instantaneous step-up in China. The step-up dry-type transformer has strong step-up capacity and good practical effect. The difference depends on that the transformer power switch without excitation regulator does not have the ability to change gear with load. Because this kind of tap power switch can cut off the whole process in a short time during the whole process of gear change, cutting off the load current will cause arc burning between circuit breakers, tap power on and off or short circuit fault, so the dry-type transformer shall be powered off during regulation. Therefore, it is generally used as a dry-type transformer that is not very strict in voltage regulation and does not need to be adjusted frequently.The raw materials of Fushi blue can be used for bonding, so that the overall oil leakage of the connector can be greatly controlled; If the actual operation is convenient,FinlandOil immersed transformer oil storage tank, the metal shell can also be bonded at the same time to achieve the purpose of leakage treatment.San-Miguelito,When using the oil sample of the power transformer in operation, it is necessary to add some oil from the oil gate valve at the lower part of the oil tank or the sampling gate valve to release about kg of waste liquid stored at the bottom to clean the oil inlet, and then take the oil sample.The iron core of power transformer is made of high-quality crystallized hot-rolled ferrite core, which is stacked at the degree fully inclined multi-step interface. The surface is covered with epoxy resin adhesive cable sheath coating, which is resistant to corrosion and rust, and has sound insulation and noise reduction.Power transformer factory
When the full load test is carried out and everything is normal, the load can be connected.The dry-type transformer used for power plant voltage transformation is different from the oil transformer. It is strictly prohibited to lead the way at the bottom voltage side to prevent the insulation layer of the dry-type transformer from penetrating due to overvoltage caused by overvoltage at the power grid side or lightning stroke on the line.What is the reason for the shutdown of power transformer?Where can I find it?,From the appearance, the packaging types are different. The transformer core and electromagnetic coil can be seen immediately for dry-type transformer and only the shell can be seen for oil immersed transformer;The oil in the machinery and equipment of the oil storage tank shall generally stand for more than h before sampling; it is not necessary to stand when sampling on the running power transformer.The method and whole process of taking oil sample of power transformer are as follows:
Dry type transformer factorymanagement,FinlandDry type transformer Market,It will also produce many faults, effectively deal with various faults of oil immersed transformer, make full use of the performance indicators and advantages of oil immersed transformer, and continuously improve the safety factor of oil immersed transformer. Ignition is a common fault of oil immersed transformer. The key fault of oil immersed transformer is short-circuit fault, and short-circuit fault is more general.When the output power P of the transformer is equivalent to the input power P, the efficiency & ETA; Equivalent, the transformer will not cause loss. But in fact, there is no such transformer. The electromagnetic energy of transformer always causes loss. The key of this kind of loss is copper loss and iron loss. Copper loss refers to the loss caused by the number of turns of transformer coil. When the current has a fever according to the number of turns of the coil, part of the electromagnetic energy changes into energy and is lost. Because the electromagnetic coil is generally wound by copper core wire with insulating layer, clean the periphery of the sampling port with clean or hairless linen.Finland,The input and output three-phase power lines shall be connected to phase a, phase B and phase C respectively according to the color of yellow, green and red bus duct of transformer terminal board. The zero line shall be connected to the neutral zero line of transformer voltage, and the grounding wire, the ground wire and zero wire are led out by the neutral wire of the transformer. (for example, the transformer box shall be matched with the ground wire mark of the shell and connected with each other). Check the input and output lines to ensure they are appropriate and accurate.Seal oil leakageTherefore, in the installation process of substation equipment, the lightning rod should be set according to the specific situation to prevent damage to the relay protection dry-type transformer caused by lightning. In addition, in the installation and use process of lightning rod, select reasonable types of lightning rod according to the operation situation to determine that they are in the same situation. In addition, during the installation of lightning rod please connect all routes as far as possible to prevent other faults.