Oil leakage of heat pipe radiatorThe noise of dry-type transformer comes fromYohevi,Dry type transformer, a static electrical equipment, is used to change the AC current (current) of a certain standard value into another or several types of working voltage (current) with the same frequency and different standard values. According to the supervision sampling inspection data of the third quarter of last year released by AQSIQ, among the kinds of dry-type transformer commodities manufactured by manufacturers in provinces and municipal districts across the country, kinds of commodities were found to be inconsistent with the provisions of relevant specifications, with a compliance rate of %& ldquo; This result mostly shows the quality level of China's dry-type transformer industry at the present stage.According to the condition of cracks, galvanized iron wire can be punched into the leakage or riveted with hammer. Then clean the leakage point with toluene and seal it with raw materials. Coated sand casting eyes can be sealed with raw materials immediately.Chernigov,YoheviPartial discharge standard for dry type transformer,YoheviOn load voltage regulation of power transformer, which can control the oscillation below .%,YoheviRecovery price of oil transformer, and then reduce the building structure noise transmitted by dry-type transformer oscillation.Due to poor sealing, generally, the sealing of box edge and machine cover is sealed with acid-base resistant rubber rod or rubber plate. If the joint is not solved well, it will lead to common faults of oil leakage.
When the transformer is out of phase, if the second phase is blocked there is still no sound when the second phase is sent, the sound will not change and there is sound when the third phase is sent; If the third phase is blocked, as in the case of the second phase. There are three reasons for phase deficiency:At that time, and the market share of high-voltage transformers was basically monopolized by overseas leaders.The manufacturing process of dry-type transformer is very process, the performance of dry-type transformer will be more stable. What are the common manufacturing processes and steps of dry-type transformer?Recommendation and consultation,Caused by sand holes and cracks. For crack leakage, drilling stop hole is a good way to remove in-situ stress and prevent widening.High voltage fuse of transformer breaks one phase;Noise pollution control and prevention measures of dry-type transformer
Sound, causing short circuit obstruction. If not handled properly, it will cause great damage.Recommendation and consultation,Under normal conditions the actual operation of the oil immersed transformer shall be undertaken by the on-site operation and maintenance management staff. Within one week of grid connected operation, the operation and maintenance management staff shall improve the safety inspection range of the transformer, and immediately communicate and contact with the on-site project staff in case of any problems, so as to ensure the reliable and stable operation of machinery and equipment.The cycle time of power-off cleaning and inspection shall be determined according to the surrounding environment and load conditions, generally from half a year to once a year;During no-load test run, the transformer shall be connected with the working voltage from the switching power supply side, and then make the working voltage impulse closing.Yohevi,The flange surface is uneven, the tightening bolts are loose, and the installation and processing process is wrong, so that the bolts are not tightened well, resulting in oil leakage.Equipped with a temperature controller, platinum thermistor (pt) is placed beside the embedded hole on the top of the low-voltage solenoid coil to test the winding resistance temperature rise of the transformer, stop the cooling centrifugal fan, set up common problem alarm, overtemperature alarm and overtemperature tripping effect, and provide reliable overvoltage protection machinery and equipment for the dry test transformer, so as to test the safety performance of the transformer operation.Gradually, high-frequency vibration damping mechanical equipment, such as low-frequency vibration damping platform, is installed at the bottom of the dry-type transformer, which can reduce the downward dispersion of the vibration of the dry-type transformer. Then replace the connection between the dry-type transformer and the surrounding engineering buildings, roads, etc. with flexible connection, or use elastic yellow shock absorption mechanical equipment to prevent the vibration from spreading according to the rigid connection. If possible, the dry-type transformer room can also be soundproofed and decorated, and sound-absorbing plates and silencing shutters can be used to improve the soundproofing capacity of the dry-type transformer room.